Image(s) and product specifications may not represent actual product and are subject to change.
Bypass an SUT30K UPS to Perform Maintenance
For use with Tripp Lite's SUT30K 3-phase UPS system, the SUT30KMBP maintenance bypass panel (MBP) maintains total continuity of power to connected load circuits when bypass of the UPS is required for regular service and maintenance. This UPS maintenance bypass panel has three 4-pole circuit breakers for Input, Bypass and Output. The breakers have removable handles to allow the panel's trim cover to be removed for internal access. The short circuit rating is 10 kAIC. Maximum current capacity is 125A.
Convenient Wall-Mount Installation
Made of galvanized steel, the service bypass panel has rear mounting holes for installation on a smooth and solid wall (mounting hardware not included).
The SUT30KMBP is backed by a one-year limited warranty, ensuring reliability and performance.
|Best selling transfer switches ranking|
|1||Tripp Lite UPS Maintenance Bypass Panel for SUT60K SUT60KMBP||$7,235.84|
|2||APC by Schneider Electric Maintenance Bypass Cabinet G35TSBP20K30F||$4,188.51|
|3||APC by Schneider Electric RACK ATS, 120V, 20A, L5-20 IN, (10) 5-20R Out AP4452||$1,146.84|
Tripp Lite SUT30K UPS
The data and images on this website have been subjected to numerous control mechanisms to ensure its' accuracy. FrontierPC.com will use best efforts to maintain its accuracy. However, if at any time the data or images provided are incorrectly priced or below fair market value or availability has substantially changed or image or descriptions contain inaccuracies, FrontierPC.com shall not be held responsible or liable, furthermore FrontierPC.com reserves the right to reject any orders placed based on this erroneous information. Copyright 2001-2019 FrontierPC.com Computer Inc., Frontier PC Canada, Frontier Computer, Toronto, Vancouver, Calgary, Halifax. All Rights Reserved.